The solution included RO-PLUS, which is a series of RO units designed for a recovery rate up to 90% while compromising neither reliability nor water quality. The result is significantly reduced running costs due to lower water and power consumption. The solution was also designed with identical I/Os, so no changes were needed in the customers' control room and it took only a very short time to connect the new controls.
A break tank and booster pumps were necessary to ensure a safe and stable water supply, as the municipal water supply had insufficient water pressure. Finally, two demi-water tanks in polypropylene enabled the production to flush and refill the rinsing basins in a short amount of time.
EUROWATER in Holland has dimensioned, supplied, installed and commissioned the complete upgrade.
- Flow: 6 m³/h
- Conductivity: < 6 μS/cm
Units in plant
- Break tank PE 13 m³
- Pump skid 15 m³/h
- Softening unit SMH 1202
- Reverse osmosis unit RO-PLUS B2-20+4 with SE30 controls
- Demi-water tanks in PP, 2 x 60 m³